1) According to the capacity of LPG vaporizer, the 2-P or 3-P cable with suitable thickness
& length must be prepared.
2) ¡°No Fuse Breaker¡± (N.F.B) is needed for safe power supplying.
3) The output connector of N.F.B is to be joined with the other side of prepared cable
without electric power connection.
4) The cover of explosion proof box on the LPG vaporizer is to be opened.
5) After inputting through the connection hole under the explosion proof box,
the cable has to be joined with terminal block which is located right side in the
explosion proof box.
6) After closing the cover, first of all, do check the LPG vaporizer whether it was filled
with water or not. And then only the case that the LPG vaporizer was filled with water,
the switch of the N.F.B shall be ¡®on¡¯ to supply the electric power, otherwise
the electric power will not be supplied.
7) Watching the thermometer on the LPG vaporizer, it must be checked whether
the thermometer is working properly. Automatically the temperature is controlled
from 608c to 708c by thermostats in the explosion proof box.